Section I. GENERAL
mendations for improving this publication by the
individual user is encouraged. Reports should be
a. This manual is for your use in installing
submitted on DA Form 2028 (Recommended
and maintaining the Grid Wire Sensor DT-
Changes to Publications) and Forwarded direct to
545( )/FSS-9(V) (Installation Kit) an integral part
Commander, U.S. Army Troop Support Command,
of the Joint-Services Interior Intrusion Detection
ATTN: AMSTS-MPP, 4300 Goodfellow Boulevard.
System (J-SIIDS). Detailed information on each of
St. Louis, MO 63120.
the other major system components is available in
b. For Air Force personnel, reporting of errors,
the applicable technical manuals listed in appendix
omissions, and recommendations for improving this
publication should be submitted on AFTO Form 22
b. This manual contains equipment description
and forwarded to HQ, SAAMA/MMSTR, Kelly AFB,
and data; installation instructions; organizational
and intermediate maintenance, direct support and
c. For Navy personnel, reporting of errors, omis-
general support instructions for troubleshooting,
sions and recommendations for improving this
and corrective maintenance; and repair parts.
publication should be submitted on Technical Man-
ual User Activity Comment Sheet and forwarded to
technical manuals, and other publications applicable
Naval Elect Systems Command, National Center
to the grid wire sensor.
Building 1, ATTN: ELEX-4903, Washington, D.C.
tion chart which list the maintenance to be per-
1-5. Destruction of Army Materiel to Prevent
will aid in the identification of authorized repair
Instructions covering the destruction of Army
materiel to prevent enemy use are contained in TM
1-2. Maintenance Forms and Records
Department of the Army forms and procedures used
for equipment maintenance will be those prescribed
1-6. Administrative Storage
by TM 38-750.
TM 740-90-1 contains instructions pertaining to
ad ministrative storage.
1-3. Equipment Serviceability Criteria (ESC)
This equipment is not covered by an ESC.
Pertinent publications on calibration of this equip-
1-4. Reporting of Errors
ment shall be referenced.
a. The reporting of errors, omissions, and recom-
Section II. DESCRIPTION AND DATA
other similar barrier, on which the grid wire sensor is
1-8. Purpose and Use
installed. The relationship of the grid wire sensor to
The grid wire sensor (Installation Kit, fig. 1-1) is used
other J-SIIDS components is illustrated in figure 1-2.
to provide a means for detecting forced entry
through a wall, floor, ceiling, door, skylight, or some