KEY to figure 2-1:
1. switch inspection window, lower
2. position indicator
3. Operating handle switch socket
4. Removable bar
Transformer. Inspect transformer for
breakers must have ; E C-1 series
any visible damage or leaks and insure gages are
over-current tripping tie vice replaced
operative. Check that the windings are connected for
for 240/416 volt service.
the desired voltage. If connections must be changed,
Low Voltage Cabinet.
d for high voltage tap changer.
(1) Open front sections and make sure
voltmeter switch, heater switch, light switch and the
three ammeter switches are in off position.
All circuit breakers are shipped for
(2) Check each breaker and make sure it is
1210 / 208 volt service. For 240 / 416
tripped and moves freely to the fully withdrawn positon
volt service the main breaker must
(1, fig. 2-2) and fully connected position (3).
have the power sensor overcurrent trip